عنوان مقاله [English]
Startup is one of the most important stages in the operation of a wastewater treatment plant (WWTP). In this paper, a novel method is presented for the startup of Arak Activated Sludge WWTP, which is shown to contain more advantages than other common methods. In this method, a portion of the inflow is initially allowed to enter gradually into an aeration basin prior to seeding. Under these conditions, less seeding is required due to the low flow of the influent and the low volume of the aeration basin. Once MLSS in the basin reaches the desired level, the rest of the system comes into operation and the sludge developed in the system is used for further seeding. In the case of the WWPT in Arak, it took about 2 months for the total MLSS to be developed and wasting the sludge to start because of the cold weather conditions in the region. The wasted sludge was controlled by the F/M ratio at a constant sludge age. During the start-up, the MLSS increase exhibited a linear trend and the low loading allowed for the variation in influent contaminants to be controlled. The effluent contaminants were below the standard levels recommended by the Environment Protection Organization. BOD5 and COD removals increased from 40% and 60% to 90% and TSS removal increased from 70% to 96%. Lower loading levels, better process control, and lower sludge processing costs are the benefits of this system
1. Van Hulle, S., Van Den Broeck, S., Maertens, J., Villez, K., Donckels, B., Schelstraete, G., Volcke E., and Vanrolleghem, P. (2005). “Construction, start-up and operation of a continuously aerated laboratory-scale SHARON reactor in view of coupling with an anammox reactor.” Water SA, 31, 327-334.
2. Jubany, I., Carrera, J., Lafuente, J., and Baeza Juan, A. (2008). “Start-up of a nitrification system with automatic control to treat highly concentrated ammonium wastewater: Experimental results and modeling.” Chemical Engineering, 144, 407-419.
3. Gali, A., Dosta, J., Mace, S., and Mata-Alvarez, J. (2006). “Start-up of a biological sequencing batch reactor to treat supernatant from anaerobic sludge digester.” Environ. Technol., 27, 891-899.
4. Wisconsin Department of Natural Resources. (2010). Advanced activated sludge study guide, Bureau of Science Services, Operator Certification Program, Washington DC, USA.
5. Huang, P., Qin, S., Zhao, Q., and Guo, X. (2006). “Quick start-up of mudanjiang wastewater treatment plant and factors influencing phosphorous removals.” Global NEST Journal, 8(1), 1-8.
6. De Maria, D., Watson, J., Oorshchot Robbert, V., and Gulovsen, T. (2006). “Commissioning of a 180 ml/day activated sludge plant at the Western treatment plant.” Werribee, 69th Annual Water Industry Engineers and Operators’ Conference, Exhibition Centre-Bendigo, 120-126.
7. Suggate, Ch. (2009). “Start-up and commissioning of a low loaded wastewater treatment plant.” 34th Annual Qld Water Industry Operation Workshop, Indoor Sports Stadium Caloundra, Australia.
8. Maillard V., Sturdevant, J., Moffett P., and Abbott D. (2008). “Start-up and initial operation of a greenfield enhanced nutrient removal wastewater treatment facility.” Water Environment Federation Technology (WEFTEC.08), 1809-1818.
9. APHA. (1991). Standard methods for the examination of water and wastewater, 17th Ed., American Publishers Health Association (APHA), AWWA., and WEF., Washington, DC, USA.
10. Tchobanoglous, G., Burton, F.L., and Stensel, H.D. (2007). Wastewater engineering treatment and reuse, 4th Ed., Metcalf and Eddy Inc., McGraw-Hill Publication, USA.
11. Iranian Environment Protection Organization (IEPO). (1990). Standard for wastewater effluent discharge limits to the environment Iran. (In Persian)
12. Bureau of Technical Affairs and Standards. (2004). Operation and maintenance guideline for municipal wastewater treatment plants, Pub No. 284, Management and Planning Organization Publications, Iran,
26-50. (In Persian)